University of Minnesota Digital Conservancy >
University of Minnesota - Twin Cities >
National Center for Earth-Surface Dynamics (NCED) >
Please use this identifier to cite or link to this item:
|Title: ||Index Test of Unit #1 Prospect Powerhouse #2|
|Authors: ||Voigt, Richard L.|
|Issue Date: ||Nov-1987|
|Publisher: ||St. Anthony Falls Laboratory|
|Series/Report no.: ||St. Anthony Falls Laboratory Project Reports|
|Abstract: ||An index test was performed September 30 and October 1, 1987, on Unit
#1 of Prospect Powerhouse #2, located near the town of Prospect, Oregon.
The testing was requested by the American Hydro Corporation and was
scheduled to be in conjunction with a possible runner upgrade of the facility.
The facility owner is Pacific Power of Portland, Oregon. The primary personnel
involved were: Mr. W. Colwill, of American Hydro Corporation;
Messr's T. O'Conner and R. Landolt of Pacific Power; Mr. R. Voigt, Jr., of
St. Anthony Falls Hydraulic Laboratory, University of Minnesota. Numerous
Pac.1f1c Power maintenance and operational personnel were also involved.
The purpose of an index tes,t is to determine the relative unit
efficiency at various wicket gate positions. Through this type of testing
the most efficient wicket gate position can be verified. This is typically
determined by varying the wicket gate position from either full gate to
closed gate or vice versa, in a series of small, usually 5 to 10%,
increments. At each position, approximately 15 to 20 parameters are
measured. Some of these parameters such as generator output and·relative
flow measurement are used in the computation of the relative efficiency
values, while others may affect turbine efficiency either directly or
|Appears in Collections:||Reports|
Items in DSpace are protected by copyright, with all rights reserved, unless otherwise indicated.